|TS6-MFMC Plate Heat Exchangers - Gasketed|
Heating of water or CIP (cleaning in place) solutions by means of steam. General heating and cooling duties.
Channels are formed between the plates and the corner ports are arranged so that the two media flow through alternate channels. The heat is transferred through the plate between the channels, and complete counter-current flow is created for highest possible efficiency. The corrugation of the plates provides the passage between the plates, supports each plate against the adjacent one and enhances the turbulence, resulting in efficient heat transfer.
The plate heat exchanger consists of a pack of corrugated metal plates with portholes for the passage of the two fluids between which heat transfer will take place.
The plate pack is assembled between a fixed frame plate and a movable pressure plate and compressed by tightening bolts. The plates are fitted with a gasket which seals the interplate channel and directs the fluids into alternate channels. The number of plates is determined by the flow rate, physical properties of the fluids, pressure drop and temperature program. The plate corrugations promote fluid turbulence and support the plates against differential pressure.
The plate and the pressure plate are fixed between upper bar and lower bar, which again is fixed to a support column.
Connections are located in the frame plate or, if either or both fluids make more than a single pass within the unit, in the frame and pressure plate.
Liquid flow rate
Up to 320 GPM, depending on media, permitted pressure drop and temperature program.
Water heating by steam
Frame and pressure plate in solid stainless steel AISI 316L
Stainless steel AISI 316L
Stainless steel AISI 316
Nitrile, EPDM or HeatSeal F™
ANSI 3", 150# studded port
Mechanical design pressure (g) / Temperature
FMC 145 psi/350°F
Maximum heat transfer surface
13 m2 (140 sq. ft)
Particulars required for quotation
- - Flow rates or heat load
- - Temperature program
- - Physical properties of liquids in question (if not water)
- - Desired working pressure
- - Maximum permitted pressure drop
- - Available steam pressure
Flow principle of a plate heat exchanger
- - Protection sheet.
- - Adjustable legs, low or high.
- - Wrench.
- - Commissioning kit, gaskets.
|H||24" - 63"||600-1600|